Enter the characters you see below Sorry, we just need to make sure you’re not a robot. Enter the characters you see below Sorry, we just need to make sure you’re not a robot. We’re sorry, uls box # 8 PDF the page you are looking for is unavailable.
The page may have been removed, had its name changed or is temporarily unavailable. Start from the UB homepage or A-Z index and try again. Or, tell us about the error because we may be able to help you. Milltronics POINTEK ULS 200 on manualslib. Milltronics POINTEK ULS 200 Instruction Manual Ultrasonic level switch. Page 2 Contact SMPI Technical Publications at the following address: Technical Publications Siemens Milltronics Process Instruments Inc.
For the library of SMPI instruction manuals, visit our Web site: www. Page 3 The Pointek ULS 200 is an excellent primary detection device, but should not be used as a backup device. For backup devices use a contacting technology such as the Pointek CLS 200. 25 A, 250 Vac Output: » repeatability: » 0. Page 6 The cover should be accessible to allow programming, wiring and display viewing. It is advisable to keep the Pointek ULS 200 away from high voltage or current runs, contactors and SCR control drives.
Page 7 Mount the ULS 200 with the sensor face at least 25 cm above the highest anticipated level. THREADED The Pointek ULS 200 is available in three thread types: 2″ NPT, 2″ BSP or PF2. Before mounting the Pointek ULS 200, insure that the mating threads are of the same type, otherwise the threads can be damaged. 3″ ANSI, DIN 65PN10 and JIS 10K 3B flanges. For Hazardous Location Model see Milltronics drawing 0-9440026Z-DI-A SANITARY The Pointek ULS 200 also comes in a sanitary version for use in the food and pharmaceutical industries.
Page 9 Mount the Pointek ULS 200 onto the top of the tank’s sanitary ferrule. Secure mating by surrounding Pointek ULS 200 the joint with the optional clamp. Tighten the adjusting nut with your hand. Page 10 INTERFACE ac Version A circuit breaker or switch in the building installation, marked as the disconnect switch, shall be in close proximity to the equipment and within easy reach of the operator. Relay contact terminals are for use with equipment having no accessible live parts and wiring having insulation suitable for at least 250 V. Page 11 INTERCONNECTION Installation shall only be performed by qualified personnel and in accordance with local governing regulations. This product is susceptible to electrostatic shock.